The audit was conducted between 12 and 27 September 2018.
The objective of the audit was to assess how they ensure compliance with the regulatory requirements pertaining to barrier management at Edvard Grieg.
Two non-conformities were identified in connection with:
• Penetrations in fire walls
• Follow-up of performance requirements for check valves and safety-critical heating cables
Three improvement points were identified in connection with:
• Passive fire protection
• Governing documents for safety systems
• Temporary equipment
Lundin has been given a deadline of 30 November 2018 to report on how non-conformities and improvement points will be addressed.